Could someone look up the MI Code about GFCI protecting Non grounded receptacles as long as they are marked 'GFCI Protected' & 'No Equipment Ground'
I have been following the NEC code on this forever and now it seems I have been corrected as that code is not accepted in MI.
I would need to run a grounded conductor (panel, water main, etc.) to add a 3 prong receptacle?
Would love to look it up myself but loaned my book out! Thanks.
Last edited by Trick440; 01/29/10 11:38 AM.