A friend is putting in a 3 phase submersible pump. His well is 720ft deep with the pump at about 700 ft. They are concerned about the torque of a large single phase pump twisting the pipe too much. It is only about a 70 foot run to the power source. He only has single phase power, so I assume there is a converter box somewhere. Is it at the well head or at the breaker. He is getting his pump this week so I should know more then, but I am just trying to get ahead and get a little info about previous experience.
Just to clarify, the starting torque of an AC motor is generally the same regardless of being 3 phase or single phase. The only thing that would make a difference in using 3 phase is if you use a VFD as a phase converter. But 700 feet is a long distance for a VFD run, so make sure your motor and VFD will not have issues with that. You may need what is called a Long Line Filter or at the very least, a reactor on the output.
It's going to be a 3hp pump. It will be his primary water supply for his house and his livestock. The county is actually helping with the cost so that he can get his animals out of and fence off the creek.
How do you deal with the excellent ground rod you just installed, with respect to lightning strikes? When you bond the power system to the well casing, you just made the rest of your electrical system very attractive to lightning.