Trick440 ,, there some figures that dont really ring the bell to me but one question will the largest motors will start the same time or not ??
for me this what i will do is figure each motor seperately
25 hp @ 208v = 74.6 amp [ i did not add 125% yet ]
74.6 +74.6 + 46.2 + 16.7 = 212.1 amps
now i will add extra 25% on largest motor which is 18.65 amp more so the total load is 230.75 amp then go with 175% for time delay fuse which it will say 402 amps but i can down size a little to even 400 amp but if you used the non time delay fuse the fuse size will jump up to 690 amp non delay fuse. the nondelayed fuse is sized at least 250% so that what it get ya on the figures
if more question just post it here
Merci , Marc
Pas de problme,il marche n'est-ce pas?"(No problem, it works doesn't it?)
This is a text book, masters exam question. There are many more with the same result and the answer in the book is definelty showing 350a feeder fuse.
As far as the 'non time delay fuse' I think that is just thrown in there. You use that for rating motor 'branch circuits'. (short circuit, GFCI protection). I'm don't think its used in the feeder calcs. But I could be wrong.
Shake n Bake
Re: Motor math question... Feeder Fuse.
#164920 06/14/0706:14 AM06/14/0706:14 AM