i have just come back to the office after being called to a property in the country side that has a propane fired generator. there appears to be no tranfer switch and the set looks in really bad condition, IE, the hose clamps for the gas connection are a bit corroded and the hose looks a bit bulging in places, i have disconnected the outgoing single phase SWA and the gas bottle.
now here comes the problem, the new owners of the property want a gen set (as the power cuts are numerous) but it not my feild of expertise,
load required; lighting = approx 6 amp, lower floor only power = approx 20 amp 2 x double outlets
any ideas on transfer switch and dis board arrangements??
gen set, gas, diesel or petrol, ? autostarter or manual,?
all help would be greatful as this client spends over 100k with us over the year.
Britspark, I havent had a great deal of experience with geny's and domestic installations; did get involved with chicken farms a good few years back had some monster geny's on them for standby power. Found Merlin Gerin (group Schnider) technical reps very helpful. Give them a shout, feel sure they will point you in the right direction. aland
Re: gen sets/domestic use#143756 08/31/0504:28 PM08/31/0504:28 PM
Someone local to here has only a diesel genset as getting mains is beyond his (artist) means. His is a slow chugger, but still quite noisey, and he finds it difficult to start sometimes so wants an electric starter.
You need to overrate gensets a fair bit, especially if they're going to be feeding a varying load, as the speed governor can interact with the load swings.
If it's a non diesel then gas is better than petrol, cleaner burning and the motor lasts longer.
Had lots of blackouts here, sometimes for 5 days, but no genset as an old anthracite aga for cooking and hot water, and a UPS for the computer do the trick.
Re: gen sets/domestic use#143757 09/02/0502:40 AM09/02/0502:40 AM
Britspark, Not sure what the fuel prices are like in your neck of the woods, but if they are anything like here, this could make for a tough choice. I would go with either Diesel or Propane. The Transfer switch will be the most expensive item and the hardest to install. Provided that the Genset gives 240VAC output you will be OK. I'd get in contact with the Power company before you do anything though, they will have rules regarding inter-connecting with thier system to make sure that there is no way that a Back-feed can happen. Manual start is the simplest and to a degree the safer option,as if there is a remote start switch, you have to have a padlock-able switch on the Genset itself, that prevents the Genset from starting while it is being worked upon, unless the remote switch can be locked out. I agree with Alan though, Tech Reps are your best source of info/help. Often these guys are not salesmen, but ex-Electricians that sought to move into that side of the field. We have an ABB rep here and he is a gold-mine of information, you don't get a sales pitch either, just knowledgeable help. You just have to ask.
Re: gen sets/domestic use#143758 09/04/0511:51 AM09/04/0511:51 AM
The simplest way to do it is to use a changeover switch with one side on the mains and the other side on a 32A surface mounted plug. Get a portable generator and a lead with one trailing socket outlet and one plug to connect to the generator when needed.
You need to provide an earth rod to comply with BS7671.
[This message has been edited by TeesdaleSparkUK (edited 09-05-2005).]
Re: gen sets/domestic use#143759 09/04/0505:30 PM09/04/0505:30 PM
I'm afraid that's not exactly the correct way to do it... I doubt you'd find a gen set with a plug on it, exposing live pins while the set is running! Basically you need a standard 32A extension cord with plug and trailing socket. Plug goes into the generator, trailing socket connects to the wall-mount socket.
Friends of mine have such a setup, transfer switch in the main panel, plug in the garage (I think 16A red CEE) and a short extension cord. 3ph generator that is powered by the tractor. Whenever there's a power outage they just switch over and fire up the generator.
Re: gen sets/domestic use#143760 09/04/0505:54 PM09/04/0505:54 PM
Um... I don't want to throw a spanner in the works but... if your client is hoping to run the fridge/freezer off that gen set, beware. My experience, in the long power cuts of the seventies, is that you need a thumping big set to start the motors of quite small refrigeration appliances- big enough in fact to run the whole house as normal. Wiring up to only run a couple of outlets and downstairs-lights adds complication to the transfer switching too, doesn't it?
Wood work but can't!
Re: gen sets/domestic use#143761 09/05/0505:32 AM09/05/0505:32 AM