As we talked last Saturday NZ / Friday nite USA time I said that I will make a thread re a worked example, so I get my old tech. notes out and have a look and refresh my own memory a bit too. there I don't deal much with PF controls at work.
Example: A 5 kW motor has a PF of 0.6 with a 240 Volts 50 Hz supply.
Find capacitance required to: a) increase the PF to unity. b) increase the PF to 0.9.
We need to know the current which flows to the cap. to work out its reactance, and with Xc we can calculate it's value in µF.
There are probably spreadsheets out for PF calculations anyway, or wholesalers who can provide assistance re the calcs.
In 3 situations the total value can also be calculated this way as long the phase voltages are used.
the total µF value found can be divided by 3 to spread the Caps over the 3 phases of the system.
In case of an installation 'unknown' the best is to get a datalogger installed for a week and analyse the PF value from the graph. Then work out what value to aim for as per utility tariffs and either do the calcs or get someone to do it to improve the PF and reduce the losses.
Cheers Ray (RODALCO)
The product of rotation, excitation and flux produces electricty.
#130272 - 02/28/0602:43 PMRe: Power Factor Calculations