The attached photos are of the CT cabinet for one of our customers. This is a new clubhouse in an age restricted community. It's hard to compete when you price for straight pipe installation.
The reason we ended up with them as a customer is that they were having problems with their parking lot lights burning out prematurely. What we found out is that there are 21 different types of HID fixtures all wired to 240V on the multi-tap ballasts. The problem is, the building (and the circuit feeding the lights) are 208V.
It's hard to compete when you try to do the right thing. The good news is that they are going to pay us to go in and repair everything correctly.
Erik, What's happening here?. This looks pretty rough, and if an apprentice did this sort of work under my supervision, there would be changes made I can assure you!. All that room and the KO's are so close. BTW, any chance of seeing what is in the box?.
[This message has been edited by Trumpy (edited 03-30-2006).]
Re: Why it's Tough to Make Money on New Construction#123473 03/30/0607:27 AM03/30/0607:27 AM
no good to see inside. it's a power company ct cabinet. I could cut the seal, but they would get a little ticked.
honestly, my guess is the foreman had minimal experience and did not speak the same language as the installer. Or they both did not care.
I don't know who did the original install, but right now the community board has us going over the entire property (common areas) with a fine tooth comb to find any problems before the builder turns everything over to them.
Re: Why it's Tough to Make Money on New Construction#123474 03/31/0610:27 AM03/31/0610:27 AM
The house I live in now was built in 2005, and I've found a few "built in a barn" quality issues here and there.. (& made the builder fix em )
1. Arc fault for the master bedroom outlets would trip as soon as anything was plugged in. I found an outlet where someone felt the need to strip about 2" off the neutral and the ground was contacting it..
2. There's an outlet in my living room thats about 3" higher than all the rest. Being it's near the fireplace I'm assuming the gasline was in the way.. I put a plant in front of it.
3. I'm not sure how this one slipped through, but there's NO switched outlet or ceiling light in the living room! (which I didn't even notice for about a month )
4. The cheapo Leviton outlets have already begun losing grip and are sporadically being replaced with Hubbell. (Now my wife complains it take too much effort to plug in her hairdryer )