Is that a 3-prong plug on 2-conductor zipcord? That makes about as much sense as the existance of plug adapters.
...actually, I'm trying hard to think of any actual codes this install broke! A (I assume) listed lamp base adapter was screwed in, and the plug adapter appears to be used correctly. And the only thing plugged in was a light. It might be skirting a requirement for a dedicated receptacle, and certainly not professional-looking, but is the installation actually unsafe?
[This message has been edited by SteveFehr (edited 01-06-2007).]
Re: Burger to Go....and Please Hurry#111574 01/06/0708:59 PM01/06/0708:59 PM
That looks like standard flat 3-conductor line cord. I would think you would want a good ground on that transformer; otherwise, the metal case (usually connected to the HV center tap) would likely float to a rather nasty voltage.
Re: Burger to Go....and Please Hurry#111575 01/06/0709:00 PM01/06/0709:00 PM