I know, this is beyond the scope of the NEC.... but when I saw these feeders, I just felt that some rule, someplace had to be violated:
(Look to right edge of frame)
Service is 800 amp single phase 240, to a commercial laundry. All feeders are like this, over entire length: insulation cracked and peeling, held in place only by the 'wrap' around the bare neutral (ASCR).
[This message has been edited by renosteinke (edited 10-08-2006).]