Definetly the work of a home owner, Wiring not supported, jacketing has been removed.and romex runs in front of the fixture. the right corner looks like someone tried to slip wires thru a small hole by removing the protective jackets
Re: Spotlight Photo#106861 12/16/0011:04 AM12/16/0011:04 AM
Looks like the unit was removed from a previous installation, nailed to the joist and connected to the romex - free air splice I guess you might call it. Almost looks like that upper nail goes right through the romex doesn't it? Guess they had to secure it within 12" of the box somehow. Do have to wonder what they have hanging from the lampholder by that wire - side of beef??