Does article 110.26 (A)(1) apply to the disconnect for the condenser unit?
or would this fall under 440.14 only required to be in sight?
I have two units with the disco mounted behind the units less than 2 feet away from the condenser..
I am thinking you need width of equipment or 30" and mounted to the left or right.
for any replies.