Found while replacing a range hood. . . .
(Sometimes handymen aren't really handy. . . .)
The sheet steel in the background is the ductwork for the range hood.
3/4" steel flex coming down from ceiling; which used to feed a cooktop.
The other end of the flex was fed from a 4 x 4 box, with feed-through cover plate, hidden/buried behind a permanently installed wall cabinet 10 feet away.
That is #10 stranded in the flex, spliced with #14 romex.
No j-box or fittings.
The romex grounds are tied to the neutral wire.
One phase fed the range hood, with a 1-amp draw. The other leg fed a duplex outlet that services the counter top.
All this fed by a double-pole 30-Amp Zinsco breaker.
- Tim T.
[This message has been edited by Webmaster (edited 05-20-2005).]