(submitted via Joe Tedesco)
Motor lug # 1 and # 2 shows a pool motor, where someone install an aluminum lug on it. Their answer to me was that the lug was UL listed or CU/AL! I also quoted to them that as per 680.26 (C) all parts must be "...stainless steel, brass,copper or copper alloy."
The next picture shows an inground pool motor wired with an extension cord with no connector. The pool was about 2 years old and we were supposed to do a "clean up" final inspection. There was also an indoor surge suppressor plug strip laying right next to the pool and the children were playing in the pool. The cords all went back to an extension cord that was draped over the house and was plugged into a receptacle in the back yard. I couldn't get a picture of it because the babysitter asked me to leave. I told her to remove the children from the pool before someone got hurt.