On a recent walk-thru I noticed the EC didn’t run separate hot, neutrals, and grounds for circuits that I indicated on my drawings.
I told the EC he needed to go back and add dedicated neutrals and grounds for the circuits indicated. This was his solution.
I questioned them about the code violation, said they never heard of that in the code.
By the way, this was the owner of the company and his lead foreman.