404.8 Accessibility and Grouping.
(A) Location. All switches and circuit breakers used as switches shall be located so that they may be operated from a readily accessible place. They shall be installed so that the center of the grip of the operating handle of the switch or circuit breaker, when in its highest position, is not more than 2.0 m (6 ft 7 in.) above the floor or working platform.
Now the only question becomes is the highest breaker in the panel being used as a switch.
[This message has been edited by tdhorne (edited 11-09-2005).]
"This alternating current stuff is just a fad. It is much too dangerous for general use" Thomas Alva Edison