Where in the 2005 code does it state that romex cannot directly feed the dishwasher(romex in wall wired directly to the dishwasher junction box)or is it just a protection issue and needs to be sleeved in flex from wall to dishwasher JB?
Loc: Michigan USA
The NEC doesn't prohibit connecting directly with NM cable but the majority of the dishwashers I inspect are cord and cap connected for three good reasons.
1. It's easier to connect a cord before they install the dishwasher and have a receptacle in the sink base cabinet to plug it into. Cord to be 3-4 feet long max. See 422.16(B)(2) 2. You now have no issues with having a disconnect at the appliance. 3. The plumber now doesn't have to deal with a hard wired connection when he/she has to pull the unit out for servicing.
ECN Electrical Forums - sponsored by Electrical Contractor Network - Electrical and Code Related Discussion for Electrical Contractors, Electricians, Inspectors, Instructors, Engineers and other related Professionals