george...thought we determined that isolated sections of steel need not be bonded
How about braided bonding jumper to the cap terminating to a lug bolted to a tapped 1/4-20 hole in the cover.
It would be better if they used a non-metalic cover with the non-metalic casing IMO.Haven't seen other than metel casings around these parts.
While were on the subject of wells, do the installations that you see have a disconnect at the casing for servicing the pump?
Most of the installations around here have no disconnect at the casing for the pump motor down in the casing and the wiring extends inside the dwelling to a location where a storage tank is, then through the pressure switch, then to the breaker in the service. The breaker at the service being the only disconnect for the installation.Wouldn't this be a violation of 430.102(B)