Thanks for the replies. The pole and meter base ocpd combo (SQD) is set to provide temp power for the site until the main panel at the house is set. It is not uncommon to have a pole with a meterbase and a disconnect on it. Almost ALL trailer parks are like that and almost all farms will have this arrangement.
There is nothing wrong with it as far as I know.
George, wouldn't the GEC have to be in the raceway or cable if this is considered a sub panel? Seeing as how it is fed from the pole I was just curious if there was anything to watch out for. Just trying to confirm.
I was just verifying what I was thinking because you have to be careful after the first OCPD with the conductors.
Thanks for the replies.
[This message has been edited by mustangelectric (edited 11-18-2004).]
Electricity has no respect for ignorance!