N1ist, Welcome to the Forum.
Congrats, Donnie, on tackling the wilds of UBB and HTML
Around here, I've come to understand that 250.110 and especially 250.114 still apply to the loads connected to GFI protected 2-wire ungrounded branch circuits. 406.3(D)(3)provides for the wiring method shown in the photo above, but when I bring in, say, a desktop computer with its grounded power supply cord, 250.114 says I still have to get the EGC connected to the power supply cord.
[This message has been edited by ElectricAL (edited 10-15-2002).]