I am currently working on a baseball field installing a new second service that will be used by part of the league. The existing 100A service has a disconnect set directly under the meter at the power pole. (The pole is about 100yds from the pressbox.) I am planning on tapping on to the existing weather head at the press box and going directly through it to the other side via conduit. Does anyone see a problem with this? We use the "3 foot" rule here in PA, which requires our panel to be located within 3 feet of where the service penetrates the wall. If the distance is further, a disconnect must be installed. I do not see any violation here since there is a disconnect already on the load side of the meter. Have I missed something?