An Excellant example!!
That's probably for defrosting the fridge!
I'm glad to hear that I'm not getting senile yet.
(although some may differ)
Also, we've talked about allowing non-gfci protected receptacles (to avoid nuisance tripping) for sump pumps located in crawl spaces, ('99 NEC 210-8(4)) but the exception that would allow it is under (5)Unfinished Basements.
Maybe We should make a collective proposal for a change? Any thoughts?
[This message has been edited by Bill Addiss (edited 12-16-2001).]