Loc: Lititz PA 17543
Can someone tell me what the difference is between the Square D breaker FA36100 and the Square D breaker FH36100? These both apparently fit the I-Line panelboards, are rated for 600 volts and have the same physical dimensions.
From what I can cipher from the catalog, for 3 phase: FH designates a 65K interrupting rating, @240V, and 25K, @277/480V and 480V; FA is good for 25K, @240V, and 18K, @ 277/480V or 480V. The "H" stands for "high interrupting rating".
ECN Electrical Forums - sponsored by Electrical Contractor Network - Electrical and Code Related Discussion for Electrical Contractors, Electricians, Inspectors, Instructors, Engineers and other related Professionals