Finished the make up today. Like I said it’s not pretty.
I had to move the CT’s. There was no way they would work where the factory put them.
Joe, the highest point of the conduits is 3.5” from the slab. Technically a violation but not enough to help this situation. The CT’s on the other hand are far less than the required 10” in table 408.10.
One other dilemma here is the parallel runs. The conduits (installed by another contractor) are 2.5Ft different in length from the longest to shortest.(longest on the right of course.
) I had to make up the difference in this section.
It’s defiantly ugly,
but code compliant.
[This message has been edited by Nick (edited 02-17-2002).]