I am helping a friend wire their house and there is going to be 14+ slope can lights. My question is can I use the junction box nn the side of the fixtures like a regular J box ? Run a feed to the fixture and run a switcg leg out or is the box just for wiring the fixture. .The fixtures are Lithonia LI6 desigened for 8" joice and there is no access from the top and they are going to be in a sheetrock ceiling. Also whwt do you think about the spring loaded wire connectors Lithonia supplies with the fixtures? Looks like a problem waiting to happen. I think i will use wire nuts instead. Some times neweris nit better. THANKS HYPRESS.
Loc: Holden, MA USA
As Larry pointed out you can do this and the wire connectors are fine. Now I have to ask why? Just run the feed to the switch box. The less work you have to overhead on a high ceiling the better. And if you should have a problem could you imagine having to go through 14 recessed fixture j boxes to find the feed. I would probably start a hunt for the person that did it!
The lights are on a 3 waw switch and for me the best way to do 3 ways is to feed the fix hot take 2 wire to the 1st switch then 3wire between switches. As far as looking fof the guy who did it I have been there too it seems that no one in this area knows how to wire anymore. Now if I could learn to type and spell life would be grate.
ECN Electrical Forums - sponsored by Electrical Contractor Network - Electrical and Code Related Discussion for Electrical Contractors, Electricians, Inspectors, Instructors, Engineers and other related Professionals