Loc: Chino Valley Az. 86323
This installation has each phase double lugged to avoid double tapping the main service feeder breaker. From the service pedestal there is a 200amp service disconnect that feeds two 100amp panels, each is fed with 2/0 THHN (yes, a tad under) and both the 2/0 are lugged together one slightly longer to accommodate the breaker. To finish the installation, each of the wires go to a separate 100amp main breaker in a 100amp panel. Please advise was this an acceptable solution to this installation? Not my install. I have not seen this before.
Loc: Bergen Co.,N.J. USA
...Generally,(2)wires under one lug is a violation,unless that lug/breaker is listed for such..as far as I know,Square D,are the only breakers whose lugs are listed for (2)wires,..but 2/0?? how did they fit (2) of them under(1)lug?? sounds fishy to me...Good Luck!! Russ
[This message has been edited by Attic Rat (edited 03-24-2005).]
.."if it ain't fixed,don't break it...call a Licensed Electrician"
Loc: Blue Collar Country
Any electrical supply house has, or can get, a variety of devices to make this sort of connection properly. One type has openings for three wires.....use with a short pigtail from the breaker. The other is a machined block with connections for two wires, and a solid 'tail' that is inserted into the breaker.
ECN Electrical Forums - sponsored by Electrical Contractor Network - Electrical and Code Related Discussion for Electrical Contractors, Electricians, Inspectors, Instructors, Engineers and other related Professionals