OHHHH NOOOOOOO!!!! They're Back Again!!!
Forgot all about those Clowns!
Thanks for the Heads-Up, Nick!
I can see $35K easilly being ripped off by these dullards!
We lost an easy $5K in one night's sweep by those Jokers - all from switchgear and service sections which were not heated up yet.
Main Breakers of >1000 Amp frames, Subfeed Breakers of >225 Amp Frames - only all < 480 VAC (240 VAC equipment).
The following crime spree was not so profitable for these bone heads - as the Transformers were live and ready.
Still did not detour them, and they tried again to steal - starting with the 1000 Amp Main Breaker for one certain section.
Must have been 1:1 Fireworks show for that Clown, once the Ratchet Wrench bolted across the Ã˜s!
500 KVA Transformer < 25 feet from Breaker; Bolted L-L-L fault: a test condition SCA calc in its best!
(very morbid thoughts from me,,, sorry!).
Must be the hazards one has to "Face"
in that "Trade"
...Pun definitely intended!