bonsoir all you guys and ladys ::
this is my first time to make new post here..
anyway can some you guys can help me with this one it reguarding about smoke alarm cr. tied with lighting cr.
but how i can deal with it being run into bedroom area . which i know they have afci requriement there. but the smoke alarm is used in every room and i tied to lighting cr. and that lighting cr have to be afci also??? i try to read the nec and i am little lost here and can you help me with this one ???
thanks for your time to read this