210.11 (C)(2) says....shall be provided to supply the bathroom receptacle outlet(s)
required by 210.52(F)....
The subtitle of 210.52 (F) is Laundry Areas
As CTwireman said
If I was the AHJ I would allow it, but that's just me. master44, give the AHJ a call, and tell them the circumstances, and if they give you a hard time ask them to "waive" it. Remember 90.4 Enforcement.
Waiving Good-Bye, and good luck,