Dean- I saw that and I would have no problem with it if the installation were not installed using CL2 cable run along side the SER cable This would not give me the wiring method of Chapter 3. I would say NM cable or any of the metal jacketed cables or EMT would be compliant. Also, unless I'm mistaken, I would need a grounding conductor.
Part of the problem is the Classification of the circuits. The manufacturer is very difficult when it comes to supplying information.
Edited by George Little (11/19/07 06:05 PM)