CTwireman, even mine has a little left to be desired, I suppose... I guess Tom's and Max Summerville's are probably up to par!
GlennH, yep, looks like "mice sign" to me!
Actually, it's one of the cleaner places around here! Getting in to the warm panel doesn't appear to be a problem for them!
Steve, yes they are, but I'm not sure if it's a violation or not... Anyone care to comment?
ThinkGood, Yup, that very one almost got in the way when I went to put the cover back on too!
Roger, LOL! What may not be clear in the pic is that the 23A or so from the sub-panel neutral and EGC is going through the metal structure of the service panel enclosure in it's hunt for the SEU neutral mounted on the ground bus on the upper left part of the panel!
The owner wasn't there at the time, and I have a sneaky feeling that the sub-panel feeds the gas pumps, floating neutral and all!!!!
What would 240V do to a 120V gas pump assuming it's probably not installed completely
[This message has been edited by sparky66wv (edited 11-10-2002).]