up n coming sparky.
with well over 20 years in this trade in england,
i have NEVER heard such utter rubbish!!!!
in no instance should a lighting circuit (domestic in 1.00mm TW/E) be placed on the same circuit as a ring main and be protected? by a 32 MCB.
point that man in our direction and we will tell him!!
or even better contact the NICEIC on 0800 013 0900 or www.niceic.org.uk!!!
they will put him right.
another question, to all of us out there,
how can that `electrician` sign off that job correctly?