The closer look helps a lot.
Is this your pet restaurant?.
However, there are a few things here that I aren't comfortable with.
The first being rigid steel conduit going into a refrigeration unit, the reason I say that John is because of vibration, here we would use a Non-metallic flexible conduit and run an extra ECC to the unit.
Secondly, that Evaporation unit should have a cover over it, a 3 sided one I mean, they run better that way.
And it keeps things from falling on the unit and jamming and burning out the fan motor.
Believe me, I've been through this rigmarole!, birds like the humming sound.
John did you do the pipe work there?.
Maybe it's the camera angle, but something looks out of square??.
Double padlocks?, I hope you've got keys mate!.
BTW, you left your steps on the roof.
[This message has been edited by Trumpy (edited 12-18-2005).]