Hello Gentlemen, here are some pix- post 'em if you want. Again I am amazed and humbled by the eagle-eyes of the ahj and the home inspector. We were here to check on a bad gfci in the kitchen for a friend of a large acct. The lady had just closed and she showed us an inspection report from the village AND a $300 report from a home inspector, dated 3 days before closing. I would guess that this was installed within last month prior to closing to comply with local code of 100A/Circuit Breakers, the dust from the tapcons was still there. There are also issues with the hvac and foundation, but that's somebody elses trouble. We replaced service panel and conductors-at least the breakers were new, the ones that weren't covered w/ #$%^@ - and grounded everything, oh-and we swapped out the fitsall, greenfield and floating gc for the A/C with emt.
Chris- chi spark
[This message has been edited by Webmaster (edited 06-24-2005).]