Thank You Trumpy
That notch in the roof was pretty close to the most mindless thing I've seen!!
Sometimes pictures just don't do justice though... 7th pic down, there's a 30A 2pole Bryant OCPD with the tie broken off & #14's on it, those panels had about 5 different makes of breakers in there, I think only one Murray MHT was new... The red Westinghouse twin breakers are older than me!
The riser hub was bolted to the blank on the top of the meter section on the last pic & he holesawed the blank (Nice rough edges for the feeders to rub on!
, I did have a hard time finding the proper oversized hub for that thing! CED special order!) No ground bar in either subpanel. in the 9th pic that white thing coming from the attic vent was a 14/2WG romex stuck in the top of one of the nema 3R subpanels with none other than a 2 screw connector... When I first saw this I thought I'd fallen asleep driving & passed the Mexican broder somehow!