There was a homemade set of instructions on the panel cover with lots of !!!! explaining the procedure. There was a 30A 240V (not 120/240V) disco for the genny above the panel. He didn't understand when I tried to explain that the feeders between the 30A disco and the panel were hot and "protected" at 200A, only #10 wire with very bad connections... No box in the house was bonded, grounds twisted together with no connector, boxes way too small (those 45º angle corner metal boxes), etc. etc. on and on... (boy I sound like a scratched record sometimes...)
He refused the work and said he'd take care of the 30A breakers himself.
How much you want to bet that they would trip 15's anyway do to overload.
How 'bout I change the subject before I become depressed?
No main disco (back to back, kinda) so the neutral is OK...
[This message has been edited by sparky66wv (edited 06-30-2001).]
5 Star Inspections