Here's what I found...
410-4(d) states that "No parts of cord connected fixtures, hanging fixtures, lighting track, pendants or ceiling-suspended (paddle) fans shall be located within a zone measured 3 ft. horizontally and 8 ft. vertically from the top of the bathtub rim or shower stall threshold..."
410-57(c) states that "A receptacle shall not be installed within a tub or shower space..." which I'm left to assume "space" is defined above in 410-4(d),
630-41(c) states that "Switches shall be located at least 5 ft., measured horizontally, from the inside walls of the spa or hot tub..."
550-8(f)(1) "Shower or Bathtub Space Receptacle outlets shall not be installed in or within reach (30 inches) of a shower or bathtub space."
(this is a double wide mobile home...)
But that's all I've found even remotely pertaining to this... I suppose it's a "legal" installation...
I'm going to steal a great question of Bill's and ask What about installing a sconce light in a shower or bathtub space? Is it legal and why(not)?
[This message has been edited by sparky66wv (edited 03-09-2001).]