Thanks to Harold Endean for these pics and info:
Here are some more violations. Pool service: I went out on an old clean up inspection. This pool wasn't finaled out( for what ever reason) anyway, I go out for a final inspection. You will see where the service panel is on the side of the hill.
Pictures 1 & 2 show the panel mounted near the pool equipment but only 24" away from the side of the cliff.
This picture shows how the hill slopes down away from the pool area.
This picture shows that there is only about 24 inches between the panel and the edge of the wall. Which is over-grown with vegetation making it slippery when wet. Also the cover opens up toward the hillside which gives you even less than 24".
This picture shows that if you do slip, the good news is that fence will catch you, however that fence is about 15-5 feet away from you straight down over rock and scrub brush.
Needless to say, this pool failed final inspection.
[This message has been edited by Trumpy (edited 05-31-2006).]