I'm not sure what sort of an idiot installed this, but they were way off the mark.
The bends in the SWA (Steel-Wire-Armoured) This message has been edited by Trumpy (edicable tend to give the show away.
Call that an explosion in a few months time.
You can't kink cables like that and expect current to flow through them, without a build up of heat.
I take it that this work was not done all at the same time, the reason I say that is because any electrician worth thier salt would protect them wires between the meters with some sort of covering.
Finger-strip from Legrand, springs to mind.
If you've ever worked in an Industrial Panel, you've seen this stuff.
The Neutral on Device C seems rather light or does it just give a neutral from Device B?.
This makes me wonder what the rest of the house looks like.
In my opinion, I don't think a lot of planning happened here.
[This message has been edited by Trumpy (edited 04-03-2006).]