I was working on a cottage recently, adding a few new circuits for a sump pump and washing machine and cleaning up some one elseâ€™s creative wiring.
The cottage has a detached shed, fed by a 3 conductor TEK, the original installer fed the TEK off of the living room lighting circuit, one of the conductors was a supply for the inside lights and plug, another was used as a switch leg so that the outside light on the shed was controlled by a switch in the living room. There is of course a neutral and EGC.
I moved the shed onto its own breaker. I was wondering on what everyoneâ€™s thoughts on how I could cover the service disconnect for this shed.